Safe Spacing Matters: Pallet Load Clearance Recommendations for Storage Rack
To minimize the risk of a pallet load and/or handling equipment colliding with a rack column or another load—creating an unsafe situation—storage rack design engineers incorporate a space allowance around the widest part of the load envelope when calculating the width and height of a storage bay opening. As explained in RMI’s Considerations for the Planning and Use of Industrial Steel Storage Racks Section 2.13.2:
Too little clearance will result in damage to both the loads and the storage racks. In an effort to minimize the damage, operators will slow down the movement of the loads and greatly add to the operating costs of the warehouse. Too much clearance will waste space and increase the costs of construction, and, in some cases, the cost of the rack system.
Because the widest part of the load envelope could be the pallet, the load (if it overhangs the pallet), or a portion of a misshapen or asymmetrical load, the clearance recommendation for a single-selective bay holding two loads is typically:
– 3 inches between the edge of the column and the edge of the widest part of the load envelope, – 6 inches between the two load envelopes, and – 6 inches between the top of the load and the bottom of the beam above it for adequate lift-off space in placement or removal.
In double-deep storage configurations, more clearance is recomended. Less clearance can be specified in push-back storage—where pallets rest on moving carts—with consideration given to the amount of overhead clearance the loads need in order to avoid interior obstructions as they travel up and down the sloped cart track.
Additionally, the National Fire Protection Association (NFPA) 13 Standard for the Installation of Sprinkler Systems requires a minimum space in the down-aisle direction between loads of 6 inches. This ensures that water can flow through the racking and better suppress a fire within the building.
This article was originally published by MHI Industry Group.